Teck 90 or Teck Style armored cables are used in industrial and commercial applications where the environment requires extra protection or durability. These cables can be direct buried and installed in conduit. HL (Hazardous Location) rated. Rated for 600/1000 volts and 90C.
Conductor: Stranded bare copper
Armor: Aluminum interlocked armor
Jacket: Inner and Outer PVC
Flame Test: UL 1581 70,000 BTU/hour flame test
Color Code: 2 Conductor: black, white – 3 Conductor: black, red, blue – 4 Conductor: black, red, blue, white – 5 Conductor and up: black with printed numbers.